SP-LR Sanitary Troubleshooting
A malfunction in a pump system may be caused by various reasons and is not necessarily the pump itself. Issues with the pipework or other fluid accessories within the system can be contributing factors. Furthermore, if the operating conditions differ too greatly from the provided specification for which the pump was selected for can also be a major contributing factor.
Consequently, it is always recommended to check the following first:
- - Has the pump been installed correctly?
- - Are the operating conditions still according to the initial specification?
- - Are the other fluid accessories within the pipework functioning correctly?
In general, the following malfunctions can be identified:
- - Pump provides little or no flow
- - Pump does not reach duty point
- - Pump provides irregular flow
- - Pump leaks
- - Pump vibrates excessively
- - Pump makes too much noise
- - Motor overheats
- - Motor cuts out on thermal overload
- - Pump has seized
Overleaf is a table of the possible causes and solutions of these malfunctions.
|X||X||X||electrical connection defective||Have qualified electrician check the electric connections|
|X||wrong rotation direction||Have qualified electrician reverse the sense of rotation of the electric motor|
|X||X||X||X||insufficient pre-pressure||Increase the pre-pressure or place the pump on a lower position|
|X||X||pump operating at the wrong speed||Check the motor speed|
|X||contaminations or objects in the pump||Clean the pump, if necessary disassemble|
|X||X||X||air in the piping||Inspect the piping|
|X||valve in suction pipe is not completely open||Entirely open the valve in the suction pipe|
|X||pump selected with too small delivery head||Install another pump|
|X||X||X||X||suction pipe or filter blocked||Clean the suction pipe or the filter|
|X||shaft seal defective||Disassemble the pump and replace the shaft seal|
|X||O-ring seal defective||Disassemble the pump and replace the O-ring seal|
|X||liquid temperature is too high||Decrease the liquid temperature|
|X||X||X||impeller is jammed||Disassemble the pump and replace the impeller|
|X||X||X||X||impeller is damaged||Disassemble the pump and replace the impeller|
|X||X||X||X||X||motor shaft is bent||Replace the motor|
|X||X||X||X||X||extension shaft is loose||Disassemble the pump, inspect the extension shaft, reassemble it and readjust.|
|X||X||X||X||X||bearings are damaged or worn||Replace the motor. For IG(F): replace the bearings|
|X||X||motor is overloaded||Check the viscosity of the liquid.|
|Switch off the motor and check if the pump does not drag. If so, disassemble the pump and repair it|